IEC 60502-1 for 0.6/1 kV COPPER CONDUCTORS, PVC INSULATED, PVC SHEATHED
IEC 60502-1 for 0.6/1 kV COPPER CONDUCTORS, PVC INSULATED, PVC SHEATHED Control Cable
kV LOW VOLTAGE CONTROL CABLES
OR XLPE INSULATED, PVC SHEATHED AS PER IEC 60502-1
Conductors shall be Circular Stranded, Class
2 as per IEC 60228, BS EN 60228. Upon request, Solid Circular Conductor,
Class 1 as per IEC 60228, BS EN 60228 can be
XLPE material and thickness shall be as per
IEC 60502-1 rated 90ºC for continuous operation or
PVC Insulation Type A as per IEC 60502-1 or
TI1 as per BS 7655 rated 70 ºC for continuous operation.
The Insulated Conductors are laid-up together
with non-hygroscopic fillers wherever necessary, the assembly is bedded
with an extruded layer of PVC. In case of
non-armoured cables, this layer may be omitted provided the outer shape of the
cable remains practically circular.
Single core : Red or Black
Two cores : Red, Black
Three cores : Red, Yellow, Blue
Four cores : Red, Yellow, Blue, Black
Five cores : Red, Yellow, Blue, Black, Green
Six cores & above : White numerals
printed on black core insulation.
• Galvanized Steel
Wires applied helically over the bedding as per IEC 60502-1 (or BS 5467, BS
6346 as per
• Double Steel
Tapes applied helically over the bedding as per IEC 60502-1.
• Copper Tape(s)
of nominal thickness 0.05mm applied helically with suitable overlap or as per
• Copper Wire
Screen (upon request) as per customer requirement.
PVC Type ST2 as per IEC 60502-1 and Type 9 as
per BS 7655 coloured Black.
Underground direct or indirect on cable tray.
Contact us if you need more details on Copper Conductor Control Cable. We are ready to answer your questions on packaging, logistics, certification or any other aspects about Power Cable for Construction、Low Voltage Control Cable. If these products fail to match your need, please contact us and we would like to provide relevant information.
Premium Related Products